| ||Format||Pages||Price|| |
|6||$45.00||  ADD TO CART|
|Hardcopy (shipping and handling)||6||$45.00||  ADD TO CART|
|Standard + Redline PDF Bundle||12||$54.00||  ADD TO CART|
Significance and Use
Control over the residue content (required by Specification D1835) is of considerable importance in end-use applications of LPG. In liquid feed systems residues can lead to troublesome deposits and, in vapor withdrawal systems, residues that are carried over can foul regulating equipment. Those that remain will accumulate, can be corrosive, and will contaminate following product. Water, particularly if alkaline, can cause failure of regulating equipment and corrosion of metals.
1.1 This test method covers the determination of extraneous materials weathering above 38°C that are present in liquefied petroleum gases. The extraneous materials will generally be dissolved in the LPG, but may have phase-separated in some instances.
1.2 Liquefied petroleum gases that contain certain anti-icing additives can give erroneous results by this test method.
1.3 Although this test method has been used to verify cleanliness and lack of heavy contaminants in propane for many years, it might not be sensitive enough to protect some equipment from operational problems or increased maintenance. A more sensitive test, able to detect lower levels of dissolved contaminants, could be required for some applications.
1.5 The values stated in SI units are to be regarded as standard. No other units of measurement are included in this standard.
1.6 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
Energy Institute DocumentIP Test Methods - Appendix A. Specifications - IP standard thermometers Available from Energy Institute, 61 New Cavendish St., London, WIG 7AR, U.K. www.energyinstpubs.org.uk
D96 Test Method for Water and Sediment in Crude Oil by Centrifuge Method (Field Procedure)
D1796 Test Method for Water and Sediment in Fuel Oils by the Centrifuge Method (Laboratory Procedure)
D1835 Specification for Liquefied Petroleum (LP) Gases
E1 Specification for ASTM Liquid-in-Glass Thermometers
ICS Number Code 75.160.30 (Gaseous fuels)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM D2158-11, Standard Test Method for Residues in Liquefied Petroleum (LP) Gases, ASTM International, West Conshohocken, PA, 2011, www.astm.orgBack to Top