Significance and Use
Samples of liquefied petroleum gases are examined by various test methods to determine physical and chemical characteristics and conformance with specifications.
Equipment described by this practice may be suitable for transportation of LPG samples, subject to applicable transportation regulations.
1.1 This practice covers equipment and procedures for obtaining a representative sample of specification Liquefied Petroleum Gas (LPG), such as specified in Specification D1835, GPA 2140, and comparable international standards.
1.2 This practice is suitable for obtaining representative samples for all routine tests for LP gases required by Specification D1835. In the event of a dispute involving sample integrity when sampling for testing against Specification D1835 requirements, Practice D3700 shall be used as the referee sampling procedure.
1.3 This practice may also be used for other Natural Gas Liquid (NGL) products that are normally single phase (NGL mix, field butane, etc.), defined in other industry specifications or contractual agreements. It is not intended for non-specification products that contain significant quantities of undissolved gases (N2, CO2), free water or other separated phases, such as raw or unprocessed gas/liquids mixtures and related materials. The same equipment can be used for these purposes, but additional precautions are generally needed to obtain representative samples of multiphase products (see Appendix X1 on Sampling Guidelines in Practice D3700).
Note 1—Practice D3700 describes a recommended practice for obtaining a representative sample of a light hydrocarbon fluid and the subsequent preparation of that sample for laboratory analysis when dissolved gases are present. Use of Practice D1265 will result in a small but predictable low bias for dissolved gases due to the liquid venting procedure to establish the 20 % minimum ullage.
1.4 This practice includes recommendations for the location of a sample point in a line or vessel. It is the responsibility of the user to ensure that the sampling point is located so as to obtain a representative sample.
1.5 The values stated in SI units are to be regarded as standard. No other units of measurement are included in this standard.
1.6 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D1835 Specification for Liquefied Petroleum (LP) Gases
D3700 Practice for Obtaining LPG Samples Using a Floating Piston Cylinder
U.S.CFR49 Transportation Available from U.S. Government Printing Office Superintendent of Documents, 732 N. Capitol St., NW, Mail Stop: SDE, Washington, DC 20401, http://www.access.gpo.gov.
liquefied petroleum gases; LPG; sampling; Butane; LPG (liquefied petroleum gases)--sampling; Manual method; Propane; Sampling gaseous materials/applications; Sampling petroleum products;
ICS Number Code 75.160.30 (Gaseous fuels)
ASTM International is a member of CrossRef.
Citing ASTM Standards
[Back to Top]