Active Standard ASTM D1125 | Developed by Subcommittee: D19.03
Book of Standards Volume: 11.01
Historical (view previous versions of standard)
Significance and Use
These test methods are applicable for such purposes as impurity detection and, in some cases, the quantitative measurement of ionic constituents dissolved in waters. These include dissolved electrolytes in natural and treated waters, such as boiler water, boiler feedwater, cooling water, and saline and brackish water.
Their concentration may range from trace levels in pure waters (1) to significant levels in condensed steam (see Test Methods D 2186 and D 4519
Where the principal interest in the use of conductivity methods is to determine steam purity, see Ref (3). These test methods may also be used for checking the correctness of water analyses (4).
1.1 These test methods cover the determination of the electrical conductivity and resistivity of water. The following test methods are included:
|Test Method A—Field and Routine Laboratory||10 to 200 000||12 to 18|
|Measurement of Static (Non-Flowing) Samples||μS/cm|
|Test Method B—Continuous In-Line Measure||5 to 200 000||19 to 23|
1.2 These test methods have been tested in reagent water. It is the user's responsibility to ensure the validity of these test methods for waters of untested matrices.
1.3 For measurements below the range of these test methods, refer to Test Method D 5391
1.4 The values stated in SI units are to be regarded as standard. No other units of measurement are included in this standard.
1.5 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. 12.1 This test method is applicable to field and routine laboratory measurements of the electrical conductivity of water using static samples. 19.1 This test method is applicable to the continuous, in-line measurement of the electrical conductivity of water.
12.1 This test method is applicable to field and routine laboratory measurements of the electrical conductivity of water using static samples.
19.1 This test method is applicable to the continuous, in-line measurement of the electrical conductivity of water.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D1066 Practice for Sampling Steam
D1129 Terminology Relating to Water
D1192 Guide for Equipment for Sampling Water and Steam in Closed Conduits
D1193 Specification for Reagent Water
D2186 Test Methods for Deposit-Forming Impurities in Steam
D2777 Practice for Determination of Precision and Bias of Applicable Test Methods of Committee D19 on Water
D3370 Practices for Sampling Water from Closed Conduits
D4519 Test Method for On-Line Determination of Anions and Carbon Dioxide in High Purity Water by Cation Exchange and Degassed Cation Conductivity
D5391 Test Method for Electrical Conductivity and Resistivity of a Flowing High Purity Water Sample
E1 Specification for ASTM Liquid-in-Glass Thermometers
ICS Number Code 13.060.60 (Examination of water for physical properties)