| ||Format||Pages||Price|| |
|PDF Version||6||$42.00||  ADD TO CART|
|Print Version||6||$42.00||  ADD TO CART|
This test method is for the determination of total sulfur in combustible fuel gases and is applicable to natural gases, manufactured gases, mixed gases, and other miscellaneous gaseous fuels. For the use of barium chloride titration following collection of sulfur dioxide by alternative procedures, ammonia, amines, substances producing water soluble cations, and fluorides will interfere with the titration. The apparatus includes the following: (1) burner, (2) chimneys, absorbers, and spray traps, (3) flow meter, (4) vacuum system, (5) air-purifying system, and (6) monometer. The schematic diagrams of the gas burner, combustion and absorption apparatus, suction system, and purified air system are provided. Reagent grade chemicals shall be used in all tests and include: (1) water, (2) denatured ethyl or isopropyl alcohol, (3) barium chloride, standard solution, (4) hydrochloric acid, (5) hydrogen peroxide, (6) iso-propanol, (7) potassium hydrogen phthalate, (8) phenolphthalein, (9) methyl orange indicator solution, (10) silver nitrate solution, (11) sodium carbonate solution, (12) sodium hydroxide solution, (13) sulfuric acid, (14) tetrahydroxyquinone indicator, and (15) thorin indicator. The procedure for the following are detailed: (1) calibration and standardization of sodium hydroxide, sulfuric acid, and barium chloride solutions, (2) preparation of apparatus, (3) sulfur determination, (4) analysis of absorbent, and (5) quality assurance. The formula of calculating the volume of gas in standard cubic feet burned during the determination and the concentration of sulfur from the results of titration are given.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
1.1 This test method is for the determination of total sulfur in combustible fuel gases, when present in sulfur concentrations between approximately 25 and 700 mg/m3 (1 to 30 grains per 100 cubic feet). It is applicable to natural gases, manufactured gases, mixed gases, and other miscellaneous gaseous fuels.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D1193 Specification for Reagent Water
ICS Number Code 75.160.30 (Gaseous fuels)
UNSPSC Code 15111500(Gaseous fuels)