Significance and Use
It is essential to sample steam representatively in order to determine the amount of all impurities (dissolved chemicals, solid particles, chemicals absorbed on solid particles, water droplets) in it (1). An accurate measure of the purity of steam provides information, which may be used to determine whether the purity of the steam is within necessary limits to prevent damage or deterioration (corrosion, solid particle erosion, flow-accelerated corrosion, and deposit buildup) of downstream equipment, such as turbines. Impurities in the steam may be derived from boiler water carryover, inefficient steam separators, natural salt solubility in the steam and other factors. The most commonly specified and analyzed parameters are sodium, silica, iron, copper, and cation conductivity.
1.1 This practice covers the sampling of saturated and superheated steam. It is applicable to steam produced in fossil fired and nuclear boilers or by any other process means that is at a pressure sufficiently above atmospheric to establish the flow of a representative sample. It is also applicable to steam at lower and subatmospheric pressures for which means must be provided to establish representative flow.
1.2 For information on specialized sampling equipment, tests or methods of analysis, reference should be made to the Annual Book of ASTM Standards, Vols 11.01 and 11.02, relating to water.
1.3 The values stated in SI units are to be regarded as standard. The values given in parentheses are for information only.
1.4 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
A269 Specification for Seamless and Welded Austenitic Stainless Steel Tubing for General Service
A335/A335M Specification for Seamless Ferritic Alloy-Steel Pipe for High-Temperature Service
D1129 Terminology Relating to Water
D3370 Practices for Sampling Water from Closed Conduits
D5540 Practice for Flow Control and Temperature Control for On-Line Water Sampling and Analysis
isokinetic sampling; sample cooler; sampling; sampling nozzles; saturated steam; superheated steam: Isokinetic sampling; Sampling water analysis applications; Saturated steam; Steam; Superheated steam; Purity analysis--water; Quality control (QC)--water;
ICS Number Code 13.060.30 (Sewage water)
ASTM International is a member of CrossRef.
Citing ASTM Standards
[Back to Top]