WITHDRAWN, NO REPLACEMENT
| ||Format||Pages||Price|| |
|4||$44.40||  ADD TO CART|
This practice covered procedures for testing concrete pipe sewer lines, when using the low-pressure air test method to demonstrate the integrity of the installed material and the construction procedures. This practice was used for testing 4 to 24-in. circular concrete pipe sewer lines utilizing gasketed joints.
Formerly under the jurisdiction of Committee C13 on Concrete Pipe, this practice was withdrawn in December 2013 with no replacement because of safety concerns when conducting this test.
1.1 This practice covers procedures for testing concrete pipe sewer lines, when using the low-pressure air test method to demonstrate the integrity of the installed material and the construction procedures. This practice is used for testing 4 to 24-in. circular concrete pipe sewer lines utilizing gasketed joints.
1.2 This practice is also used as a preliminary test to enable the installer to demonstrate the condition of the line prior to backfill.
1.3 A complete metric companion to Practice C 924 has been developed—C 924M; therefore, no metric equivalents are presented in this practice.
Note 1—The user of this practice is advised that air test criteria presented in this practice are similar to those in general use. The test and criteria have been used widely and successfully in testing smaller diameter pipe, but additional data are required to confirm the safety and applicability or develop criteria for pipe larger than 24 in. in diameter. Larger pipe will be accepted more conveniently by visual inspection and individual joint testing.
Note 2—The user of this practice is advised that no correlation has been found between air loss and water leakage.
1.4 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use (see Section 6, Safety Precautions).
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
C822 Terminology Relating to Concrete Pipe and Related Products
C969 Practice for Infiltration and Exfiltration Acceptance Testing of Installed Precast Concrete Pipe Sewer Lines