Active Standard ASTM C828 | Developed by Subcommittee: C04.20
Book of Standards Volume: 04.05
Historical (view previous versions of standard)
This test method contains procedures using low-pressure air for testing the integrity of installed vitrified clay pipe lines such as gravity-flow sewer pipes. The procedures detailed here should be performed on lines after adequately and properly plugging and bracing connection laterals, if any, and after the trenches are backfilled for a sufficient time. This test method can also be used as a preliminary test to demonstrate the condition of the line prior to backfill and further construction activities.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
1.1 This test method defines procedures for testing vitrified clay pipe lines, using low-pressure air, to demonstrate the integrity of the installed line. Refer to Practice C12.
1.2 This test method shall be performed on lines after connection laterals, if any, have been plugged and braced adequately to withstand the test pressure, and after the trenches have been backfilled for a sufficient time to generate a significant portion of the ultimate trench load on the pipe line. The time between completion of the backfill operation and low-pressure air testing shall be determined by the approving authority.
1.3 This test method may also be used as a preliminary test, which enables the installer to demonstrate the condition of the line prior to backfill and further construction activities.
1.4 This test method is suitable for testing gravity-flow sewer pipe constructed of vitrified clay or combinations of clay and other pipe materials.
1.5 Terminology C896 is to be used for clarification of terminology in this test method.
1.6 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.
1.7 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
C12 Practice for Installing Vitrified Clay Pipe Lines
C896 Terminology Relating to Clay Products
C1091 Test Method for Hydrostatic Infiltration Testing of Vitrified Clay Pipe Lines
ICS Number Code 23.040.01 (Pipeline components in general. Pipelines)