| ||Format||Pages||Price|| |
|4||$39.00||  ADD TO CART|
|Hardcopy (shipping and handling)||4||$39.00||  ADD TO CART|
|Standard + Redline PDF Bundle||8||$46.80||  ADD TO CART|
This specification covers extra strength and standard strength vitrified clay pipe and fittings to be used for the conveyance of sewage, industrial wastes, and storm water; and extra strength perforated and standard strength perforated vitrified clay pipe to be used for underdrainage, filter fields, leaching fields, and similar subdrainage installations. Vitrified clay pipe shall be manufactured from fire clay, shale, surface clay, or a combination of these materials that, when formed into pipe and fired to suitable temperatures. Pipe shall meet the bearing strength requirements prescribed. The manufacturer shall at his option, apply either a hydrostatic pressure test or an absorption test to all of the test specimens in each size and run of the pipe. The absorption of vitrified clay pipe shall not exceed 8%. The acid resistance test is used to determine the resistance of pipe to the action of acids encountered in sanitary sewers.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
1.1 This specification establishes the criteria for acceptance, prior to installation, of extra strength and standard strength vitrified clay pipe and fittings to be used for the conveyance of sewage, industrial wastes, and storm water; and extra strength perforated and standard strength perforated vitrified clay pipe to be used for underdrainage, filter fields, leaching fields, and similar subdrainage installations.
1.2 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.
1.3 The following precautionary caveat pertains only to the Test Method portion, 5.2-126.96.36.199 of this standard: This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
C301 Test Methods for Vitrified Clay Pipe
C425 Specification for Compression Joints for Vitrified Clay Pipe and Fittings
C828 Test Method for Low-Pressure Air Test of Vitrified Clay Pipe Lines
C896 Terminology Relating to Clay Products
C1091 Test Method for Hydrostatic Infiltration Testing of Vitrified Clay Pipe Lines
ICS Number Code 23.040.50 (Pipes and fittings of other materials)
ASTM C700-13, Standard Specification for Vitrified Clay Pipe, Extra Strength, Standard Strength, and Perforated, ASTM International, West Conshohocken, PA, 2013, www.astm.orgBack to Top