This specification covers the classification, composition, physical properties, and dimensions of mineral fiber (rock, slag, or glass) blanket intended for use as thermal insulation on surfaces at certain temperatures. The orientation of the fibers within the blanket is primarily parallel to the principal surface (face). The mineral fiber blanket insulation shall be classified into seven types: Types I, II, III, IV, V, VI, and VII. The classification is based upon the insulations' maximum use temperature and apparent thermal conductivity. Mineral fiber blanket insulation shall be composed of rock, slag, or glass processed from the molten state into fibrous form bonded with an organic or inorganic binder, or both. Asbestos shall not be used as an ingredient or component part of the product. Different test methods shall be performed on the insulation to determine the following properties: odor emission, corrosiveness to steel, non-fibrous content, maximum use temperature, maximum exothermic temperature rise, apparent thermal conductivity, water vapor sorption, flexibility, rigidity, and surface burning characteristics.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
1.1 This specification covers the classification, composition, physical properties, and dimensions of mineral fiber (rock, slag, or glass) blanket intended for use as thermal insulation on surfaces operating at temperatures between 0°F (-18°C) and 1200°F (649°C). For specific applications, the actual temperature limits shall be agreed upon between the supplier and the purchaser.
1.2 The orientation of the fibers within the blanket is primarily parallel to the principal surface (face). This specification does not cover fabricated pipe and tank wrap insulation where the insulation has been cut and fabricated to provide a fiber orientation that is perpendicular to the surface (face).
1.3 For satisfactory performance, properly installed protective vapor retarders must be used in below ambient temperature applications to reduce movement of water vapor through or around the insulation towards the colder surface. Failure to use a vapor retarder can lead to insulation and system damage. Refer to Practice C921 to aid material selection. Although vapor retarders are not part of this specification, properties required in Specification C1136 are pertinent to application or performance.
1.4 This standard does not purport to provide the performance requirements of hourly-rated fire systems. Consult the manufacturer for the appropriate system.
1.5 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.
1.6 This standard does not purport to address all of the safety concerns associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
C167 Test Methods for Thickness and Density of Blanket or Batt Thermal Insulations
C168 Terminology Relating to Thermal Insulation
C177 Test Method for Steady-State Heat Flux Measurements and Thermal Transmission Properties by Means of the Guarded-Hot-Plate Apparatus
C390 Practice for Sampling and Acceptance of Thermal Insulation Lots
C411 Test Method for Hot-Surface Performance of High-Temperature Thermal Insulation
C447 Practice for Estimating the Maximum Use Temperature of Thermal Insulations
C518 Test Method for Steady-State Thermal Transmission Properties by Means of the Heat Flow Meter Apparatus
C665 Specification for Mineral-Fiber Blanket Thermal Insulation for Light Frame Construction and Manufactured Housing
C680 Practice for Estimate of the Heat Gain or Loss and the Surface Temperatures of Insulated Flat, Cylindrical, and Spherical Systems by Use of Computer Programs
C795 Specification for Thermal Insulation for Use in Contact with Austenitic Stainless Steel
C921 Practice for Determining the Properties of Jacketing Materials for Thermal Insulation
C1045 Practice for Calculating Thermal Transmission Properties Under Steady-State Conditions
C1058 Practice for Selecting Temperatures for Evaluating and Reporting Thermal Properties of Thermal Insulation
C1101/C1101M Test Methods for Classifying the Flexibility or Rigidity of Mineral Fiber Blanket and Board Insulation
C1104/C1104M Test Method for Determining the Water Vapor Sorption of Unfaced Mineral Fiber Insulation
C1114 Test Method for Steady-State Thermal Transmission Properties by Means of the Thin-Heater Apparatus
C1136 Specification for Flexible, Low Permeance Vapor Retarders for Thermal Insulation
C1304 Test Method for Assessing the Odor Emission of Thermal Insulation Materials
C1335 Test Method for Measuring Non-Fibrous Content of Man-Made Rock and Slag Mineral Fiber Insulation
C1338 Test Method for Determining Fungi Resistance of Insulation Materials and Facings
E84 Test Method for Surface Burning Characteristics of Building Materials
Other Referenced Documents
blanket; glass fiber; high temperature; mineral fiber insulation; rock fiber; shot; shot content; slag fiber; Blanket thermal insulation--specifications; Industrial buildings/developments--specifications; Mineral fiber insulation--specifications; Odor--thermal insulation materials; Sensory analysis--odor; Water absorption--thermal insulating materials;
ICS Number Code 91.100.60 (Thermal and sound insulating materials)
ASTM International is a member of CrossRef.
Citing ASTM Standards
[Back to Top]