Active Standard ASTM C500 / C500M | Developed by Subcommittee: C17.03
Book of Standards Volume: 04.05
Historical (view previous versions of standard)
This test method covers the standard for testing of asbestos-cement pipe for hydrostatic strength, flexural strength, crushing strength, straightness, and uncombined calcium hydroxide. Hydrostatic pressure test is performed by placing the pipe with a factory-assembled joint, in a hydrostatic pressure testing machine. Air is expelled and an internal water pressure at a uniform rate is applied. The flexural strength test is performed by supporting the pipe in a flexural testing machine and distributing the load equally, and applying the load at the third points of the clear span. The crushing test shall be performed using the V-shaped bearing method. The straightness test is performed by determining the outer diameter of each pipe at both ends and in the middle and calculating the differences in outer diameter.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
1.1 These test methods cover the testing of asbestos-cement pipe for hydrostatic strength, flexural strength, crushing strength, straightness, and uncombined calcium hydroxide; they are for use in conjunction with the individual product specifications for asbestos-cement pipe.
1.2 Test methods appear in the following sections:
|Hydrostatic Pressure Test||4|
|Uncombined Calcium Hydroxide Test||8|
1.3 Guidelines for internal and external corrosion included in Section 9 serve as an aid in determining the type of pipe which should be specified to maximize service life for a particular application.
1.4 The values stated in either SI units or inch-pound units are to be regarded separately as standard. The values stated in each system may not be exact equivalents; therefore, each system shall be used independently of the other. Combining values from the two systems may result in non-conformance with the standard.
1.6 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. For a specific safety hazard, see 1.5. ^REFERENCE:
D1067 Test Methods for Acidity or Alkalinity of Water
D1126 Test Method for Hardness in Water
D2946 Terminology for Asbestos and Asbestos–Cement Products
E11 Specification for Woven Wire Test Sieve Cloth and Test Sieves
E200 Practice for Preparation, Standardization, and Storage of Standard and Reagent Solutions for Chemical Analysis
BNQ 3807-098 Vulcanized Rubber: Hardness Determination
Regulation No. 3, Formula for Completely and Specifically Denatured Alcohol
ICS Number Code 23.040.50 (Pipes and fittings of other materials)