| ||Format||Pages||Price|| |
|7||$43.00||  ADD TO CART|
|Hardcopy (shipping and handling)||7||$43.00||  ADD TO CART|
|Standard + Redline PDF Bundle||14||$51.60||  ADD TO CART|
Significance and Use
In this practice it is recognized that effectiveness, safety, and durability of an RBS depends not only on the quality of the materials, but also on proper installation.
Improper installation of an RBS will reduce the thermal effectiveness, cause fire risks and other unsafe conditions, and promote deterioration of the structure in which it is installed. Improper installations include fires caused by: (1) heat buildup in recessed lighting fixtures, (2) deterioration or failure of electrical wiring components, and (3) deterioration in wood structures and paint failure as a result of moisture accumulation.
This practice provides direction for the installation of RBS products in a safe and effective manner. Actual conditions in existing buildings vary greatly and care shall be taken to ensure safe and effective installation.
In this practice, requirements are presented that are both general and specific in nature and practical. They are not intended as specific instructions unless so indicated. The user shall consult the manufacturer for application and installation methods. The requirements in this practice shall be the minimum material and installation requirements for RBS.
1.1 This practice has been prepared for use by the designer, specifier, builder, and the installer of radiant barrier systems (RBS) for use in commercial/industrial building construction not otherwise restricted from use. The scope is limited to instruction relative to the use and installation of RBS, including a surface(s) normally having an emittance of 0.1 or less, such as metallic foil or metallic foil deposits, mounted on substrates. Some examples that this practice is intended to address include: (1) low-emittance surfaces in vented building envelope cavities intended to retard radiant transfer across the airspace: (2) low-emittance surfaces at interior building surfaces intended to retard radiant transfer to, or from, building inhabitants; and (3) low-emittance surface at interior building surfaces intended to reduce radiant transfer to, or from, radiant heating or cooling systems.
1.2 This practice covers the installation process from pre-installation inspection through the post-installation procedure. It does not cover the production of the radiant barrier materials. (See Specification C1313.)
1.3 This practice is not intended to replace the manufacturer’s installation instructions but shall be used in conjunction with such instructions. This practice is not intended to supercede local, state, federal, or international codes.
1.4 This practice assumes that the installer possesses a good working knowledge of the applicable codes and regulations, safety practices, tools, equipment, and methods necessary for installation of radiant barrier materials. It also assumes that the installer understands the fundamentals of commercial/industrial building construction that affect the installation of RBS.
1.5 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.
1.6 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. For specific precautionary statements see Sections 5 and 7.
1.6.1 When the installation or use of radiant barrier materials, accessories, and systems has the potential to pose safety or health problems, the manufacturer shall provide the user appropriate current information regarding any known problems associated with the use of the product of the company and shall also specify protective measures.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
C168 Terminology Relating to Thermal Insulation
C1313 Specification for Sheet Radiant Barriers for Building Construction Applications
NFPA StandardsNFPA211 Standard for Chimneys, Fireplaces and Vents
Other DocumentCPSC Product Safety Fact Sheet No. 18 The Home Electrical System
ICS Number Code 91.120.99 (Other standards related to protection of and in buildings)
UNSPSC Code 30000000(Structures and Building and Construction and Manufacturing Components and Supplies)
ASTM C1744-12, Standard Practice for Installation and Use of Radiant Barrier Systems (RBS) in Commercial/Industrial Building Construction, ASTM International, West Conshohocken, PA, 2012, www.astm.orgBack to Top