| ||Format||Pages||Price|| |
|26||$62.00||  ADD TO CART|
|Hardcopy (shipping and handling)||26||$62.00||  ADD TO CART|
|Standard + Redline PDF Bundle||52||$74.40||  ADD TO CART|
Significance and Use
4.2 The long-term applicability of a remotely operated radiological facility will be greatly affected by the provisions for remote viewing of normal and off-normal operations within the facility. The deployment of remote viewing systems can most efficiently be addressed during the design and construction phases.
4.2.2 It is intended that this guide record the general conditions and practices that experience has shown are necessary to minimize equipment failures and maximize the effectiveness and utility of remote viewing equipment. It is also intended to inform designers and engineers of those features that are highly desirable for the selection of equipment that has proven reliable in high radiation environments.
1.1.1 This guide establishes the minimum requirements for viewing systems for remotely operated facilities, including hot cells (shielded cells), used for the processing and handling of nuclear and radioactive materials. The intent of this guide is to aid in the design, selection, installation, modification, fabrication, and quality assurance of remote viewing systems to maximize their usefulness and to minimize equipment failures.
1.1.2 It is intended that this guide record the principles and caveats that experience has shown to be essential to the design, fabrication, installation, maintenance, repair, replacement, and, decontamination and decommissioning of remote viewing equipment capable of meeting the stringent demands of operating, dependably and safely, in a hot cell environment where operator visibility is limited due to the radiation exposure hazards.
1.2.1 This guide applies to, but is not limited to, radiation hardened and non-radiation hardened cameras (black- and-white and color), lenses, camera housings and positioners, periscopes, through wall/roof viewing, remotely deployable cameras, crane/robot mounted cameras, endoscope cameras, borescopes, video probes, flexible probes, mirrors, lighting, fiber lighting, and support equipment.
22.214.171.124 The facility equipment can neither be accessed directly for purposes of operation or maintenance, nor can the equipment be viewed directly, for example, without shielding viewing windows, periscopes, or a video monitoring system.
1.2.3 The remote viewing equipment may be intended for either long-term application (commonly, in excess of several years) or for short-term usage (for example, troubleshooting). Both types of applications are addressed in sections that follow.
1.2.5 The system of units employed in this guide is the metric unit, also known as SI Units, which are commonly used for International Systems, and defined by ASTM/IEEE SI 10, Standard for Use of International System of Units. Some video parameters use traditional units that are not consistent with SI Units but are used widely across the industry. For example, video image format is referred to in “inch” units. (See Table 1.)
1.2.6 Lens and lens element measurements are always in millimeter (mm) units, even where SI Units are not in common usage, as an industry practice. Other SI Units (for example, cm) are rarely used for lenses or lens elements.
1.3.1 This guide does not cover radiation shielding windows used for hot cell viewing. They are covered separately under Guide C1572.
1.3.3 The guidance set forth in this guide relating to design of equipment is intended only to inform designers and engineers of these features, conditions, and procedures that have been found necessary or highly desirable to the design, selection, operation and maintenance of reliable remote viewing equipment for the subject service conditions.
1.3.4 The guidance set forth in this guide results from operational experience of conditions, practices, features, lack of features, or lessons learned that were found to be sources of operating or maintenance problems, or causes of failure.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
C1217 Guide for Design of Equipment for Processing Nuclear and Radioactive Materials
C1533 Guide for General Design Considerations for Hot Cell Equipment
C1554 Guide for Materials Handling Equipment for Hot Cells
C1572 Guide for Dry Lead Glass and Oil-Filled Lead Glass Radiation Shielding Window Components for Remotely Operated Facilities
E170 Terminology Relating to Radiation Measurements and Dosimetry
ICS Number Code 25.040.30 (Industrial robots. Manipulators); 37.020 (Optical equipment)
UNSPSC Code 52161525(Remote control); 73171603(Photographic or optical equipment manufacture services)
ASTM C1661-13, Standard Guide for Viewing Systems for Remotely Operated Facilities, ASTM International, West Conshohocken, PA, 2013, www.astm.orgBack to Top