| ||Format||Pages||Price|| |
|4||$38.00||  ADD TO CART|
|Hardcopy (shipping and handling)||4||$38.00||  ADD TO CART|
|Standard + Redline PDF Bundle||8||$45.60||  ADD TO CART|
This specification covers fabrication techniques for cellular glass block into billets to fabricate pipe and tubing insulation. The optimization of the thermal performance of installed cellular glass insulation systems is discussed. This is best achieved by limiting the number of joints, in particular through joints. Cellular glass pipe and tubing insulation shall be fabricated from the minimum number of insulation blocks. Sectional pipe insulation shall contain not more than four through joints per full section of insulation, excluding the half section mating plane. Fabrication adhesive shall be hot asphalt, Type II operating at some temperature. For operating temperatures above ambient, fabrication adhesive shall include but not be limited to Type II hot asphalt, elastomeric asphalt, or gypsum-based cement of the type and grade specified. Fabricating adhesive shall be applied such that there is 100% coverage of adhesive on the mating surfaces. Billet and miter construction shall conform to the following: insulation blocks or sections shall be hand rubbed if necessary to fit prior to bonding and bond joints shall be made with a full depth of approved adhesive. Bond joints can be classified as “non-through“ joints which start at the outside circumference and run continuously in a straight line to the opposite side terminating at the outside circumference. “Through” joints start at the outside circumference and runs continuously in a straight line to the opposite side and terminates at the inside circumference. All segmented pipe insulation shall be edge trimmed at the fabrication site. Either a grinder or a saw shall be used to edge trim segmented pipe insulation. If segmented pipe insulation is edge trimmed using a saw blade, edges shall be rubbed to remove uneven patterns caused by flexing blade where needed. Fittings for all sizes shall be either factory ground or factory mitered.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
1.1 This specification covers fabrication techniques for cellular glass block into billets to fabricate pipe and tubing insulation. All materials shall be in accordance with Specification C552.
1.2 The purpose of this specification is to optimize the thermal performance of installed cellular glass insulation systems. This is best achieved by limiting the number of joints, in particular through joints.
1.3 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.
1.4 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
C168 Terminology Relating to Thermal Insulation
C450 Practice for Fabrication of Thermal Insulating Fitting Covers for NPS Piping, and Vessel Lagging
C552 Specification for Cellular Glass Thermal Insulation
C585 Practice for Inner and Outer Diameters of Thermal Insulation for Nominal Sizes of Pipe and Tubing
D312 Specification for Asphalt Used in Roofing
ICS Number Code 23.040.99 (Other pipeline components); 81.040.30 (Glass products)
UNSPSC Code 30141500(Thermal insulation)
ASTM C1639-10a, Standard Specification for Fabrication of Cellular Glass Pipe and Tubing Insulation, ASTM International, West Conshohocken, PA, 2010, www.astm.orgBack to Top