Active Standard ASTM C1374 | Developed by Subcommittee: C16.32
Book of Standards Volume: 04.06
Historical (view previous versions of standard)
Significance and Use
This test method was designed to give the manufacturer of loose-fill insulation products a way of determining what the initial installed thickness should be in a horizontal open attic for pneumatic applications.
The installed thickness value developed by this test method is intended to provide guidance to the installer in order to achieve a minimum mass/unit area for a given R-value.
For the purpose of product design, testing should be done at a variety of R-values. At least three R-values should be used: the lowest R-value on the product label, the highest R-value on the product label, and an R-value near the midpoint of the R-value range.
Note 1—For quality control purposes, testing may be done at one R-value of R-19 (h×ft2×°F/Btu) or higher.
Specimens are blown in a manner consistent with the intended installation procedure. Blowing machine settings should be representative of those typically used for field application with that machine.
The material blown for a given R-value as part of the installed thickness test equals the installed mass/unit area times the test chamber area. This mass can be calculated from information provided on the package label at the R-value prescribed.
1.1 This test method covers determination of the installed thickness of pneumatically applied loose-fill building insulations prior to settling by simulating an open attic with horizontal blown applications.
1.2 This test method is a laboratory procedure for use by manufacturers of loose-fill insulation for product design, label development, and quality control testing. The apparatus used produces installed thickness results at a given mass/unit area.
1.4 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.
1.5 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
C168 Terminology Relating to Thermal Insulation
C520 Test Methods for Density of Granular Loose Fill Insulations
C739 Specification for Cellulosic Fiber Loose-Fill Thermal Insulation
C764 Specification for Mineral Fiber Loose-Fill Thermal Insulation
E691 Practice for Conducting an Interlaboratory Study to Determine the Precision of a Test Method
ICS Number Code 91.100.60 (Thermal and sound insulating materials); 91.120.10 (Thermal insulation of buildings)
UNSPSC Code 30141500(Thermal insulation)