| ||Format||Pages||Price|| |
|2||$38.00||  ADD TO CART|
|Hardcopy (shipping and handling)||2||$38.00||  ADD TO CART|
|Standard + Redline PDF Bundle||4||$45.60||  ADD TO CART|
Significance and Use
5.1 This is not a routine test. The values recorded are applicable only to the sewer being tested and at the time of testing.
1.1 This practice covers procedures for testing the joints of installed precast concrete pipe sewer lines, when using either air or water under low pressure to demonstrate the integrity of the joint and the construction procedures. This practice is used for testing 675-mm and larger diameter precast concrete sewer lines utilizing rubber gasket sealed joints.
Note 1: The user of this practice is advised that methods described herein may also be used as a preliminary test to enable the manufacturer or installer to demonstrate the condition of sewer pipe prior to delivery.
1.2 This practice is the SI companion of Practice .
Note 2: The owner shall specify the following: who will conduct, observe, and furnish labor, material, and measuring devices and pay for the tests; who is responsible for determining local ground conditions; and whether an air or water test is to be used.
Note 3: The user of this practice is advised that test criteria presented in this practice are similar to those in general use. Pipe shall be accepted by infiltration or exfiltration testing utilizing Practice .
Note 4: Test times tabulated and the rate of air loss in this standard are based on successful testing of installed pipelines. However, since air and water have different physical properties, retests of some pipelines not meeting field air tests have been successful when tested with water.
1.3 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. Specific safety precautions are given in Section .
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
C822 Terminology Relating to Concrete Pipe and Related Products
C924M Practice for Testing Concrete Pipe Sewer Lines by Low-Pressure Air Test Method (Metric)
C969M Practice for Infiltration and Exfiltration Acceptance Testing of Installed Precast Concrete Pipe Sewer Lines (Metric)
ICS Number Code 23.040.50 (Pipes and fittings of other materials)
UNSPSC Code 30103619(Precast concrete element)
ASTM C1103M-14, Standard Practice for Joint Acceptance Testing of Installed Precast Concrete Pipe Sewer Lines (Metric), ASTM International, West Conshohocken, PA, 2014, www.astm.orgBack to Top