| ||Format||Pages||Price|| |
|3||$39.00||  ADD TO CART|
|Hardcopy (shipping and handling)||3||$39.00||  ADD TO CART|
This specification covers splash bar and corrugated sheet type asbestos-cement products used as cooling tower fill. This specification does not apply to the following: drift eliminators or demisters, louvers, partitioning and casing panels; asbestos-cement pipes; and asbestos-cement flat sheet fill (heat exchange surfaces). Splash bars are classified into the following types: Type I, splash bars consisting of corrugated autoclaved pressed asbestos-cement sheets for the most demanding applications; Type II, splash bars consisting of corrugated pressed asbestos-cement sheets for intermediate service; and Type III, splash bars intended for less demanding service. The corrugated fill used shall be of Type A, which are non-autoclaved, compressed, corrugated sheet with a specified nominal thickness. Materials shall conform to specified manufacturing (autoclave, pressing, and nominal thickness), composition (cement:silica ratio, mineral diluents, cellulose, maximum organic content, and cement type), and performance (apparent density, water absorption, bending moment, freeze-thaw resistance, Harkort test, and free lime) requirements.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
1.1 This specification covers splash bar and corrugated sheet type asbestos-cement products used as cooling tower fill.
1.2 Drift eliminators or demisters, louvers, partitioning and casing panels are covered in Specifications . Asbestos-cement pipes are covered in Specification and Specifications . Asbestos-cement flat sheet fill (heat exchange surfaces) are specified in Specification .
1.3 The values stated in the SI system are to be regarded as the standard. The inch-pound units in parentheses are for information only.
1.4 Warning—Breathing of asbestos dust is hazardous. Asbestos and asbestos products present demonstrated health risks for users and for those with whom they come into contact. In addition to other precautions, when working with asbestos-cement products, minimize the dust that results. For information on the safe use of chrysoltile asbestos, refer to “Safe Use of Chrysotile Asbestos: A Manual on Preventive and Control Measures.”
1.5 The following precautionary caveat pertains only to the Test Method portion, Section , of this Specification: This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. See for a specific safety hazard.
ICS Number Code 91.100.40 (Products in fibre-reinforced cement)
UNSPSC Code 30111601(Cement); 40101716(Cooling tower)
|Link to Active (This link will always route to the current Active version of the standard.)|
ASTM C1081-98(2014), Standard Specification for Asbestos-Cement Corrugated Fill For Use in Cooling Towers, ASTM International, West Conshohocken, PA, 2014, www.astm.orgBack to Top