This specification establishes the requirements for welded copper for air conditioning and refrigeration service for use in connections, repairs, and alterations. The material of manufacture shall be sheet or strip of Copper Alloy UNS No. C10100, or C10200, or C12000, or C12200 of such purity and soundness as to be suitable for processing into welded tube to meet the properties prescribed. The product shall be manufactured by forming the material into a tubular shape on a suitable forming mill and welded using an automatic process. The product shall be cold worked to the finished size and wall thickness and subsequently annealed to meet the temper properties specified. The material shall conform to the chemical compositional requirements for the Copper UNS No. designation specified. Tensile strength test, expansion test, microscopical examination, hydrogen embrittlement susceptibility, flattening test, reverse bend test, electromagnetic test, and cleanness test shall be made to conform to specified requirements.
This abstract is a brief summary of the referenced standard. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date.
1.1 This specification establishes the requirements for welded copper tube for air conditioning and refrigeration service for use in connections, repairs, and alterations. The tube shall be made from one of the following coppers:
Copper UNS No.
Previously Used Designation
Type of Copper
Oxygen-free without-residual oxidants
Phosphorus-deoxidized, low-residual phosphorus
Phosphorus-deoxidized, high-residual phosphorus
—Fittings used for soldered or brazed connections in air conditioning and refrigeration systems are described in ASME Standard B 16.22.
—The assembly of copper tubular systems by soldering is described in Practice B828.
—Solders for joining copper tubular systems by descirbed in Specification B32. The requirements for acceptable fluxes for these systems are described in Specification B813.
1.2 Copper UNS No. C12200 shall be furnished, unless otherwise specified. The copper tube shall be supplied in annealed coils or drawn temper straight lengths.
1.3 Units—Values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units which are provided for information only and are not considered standard.
1.4 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
B32 Specification for Solder Metal
B153 Test Method for Expansion (Pin Test) of Copper and Copper-Alloy Pipe and Tubing
B170 Specification for Oxygen-Free Electrolytic Copper--Refinery Shapes
B577 Test Methods for Detection of Cuprous Oxide (Hydrogen Embrittlement Susceptibility) in Copper
B601 Classification for Temper Designations for Copper and Copper Alloys--Wrought and Cast
B813 Specification for Liquid and Paste Fluxes for Soldering of Copper and Copper Alloy Tube
B828 Practice for Making Capillary Joints by Soldering of Copper and Copper Alloy Tube and Fittings
B846 Terminology for Copper and Copper Alloys
B900 Practice for Packaging of Copper and Copper Alloy Mill Products for U.S. Government Agencies
B968/B968M Test Method for Flattening of Copper and Copper-Alloy Pipe and Tube
E3 Guide for Preparation of Metallographic Specimens
E8/E8M Test Methods for Tension Testing of Metallic Materials
E29 Practice for Using Significant Digits in Test Data to Determine Conformance with Specifications
E53 Test Method for Determination of Copper in Unalloyed Copper by Gravimetry
E62 Test Methods for Chemical Analysis of Copper and Copper Alloys (Photometric Methods)
E243 Practice for Electromagnetic (Eddy-Current) Examination of Copper and Copper-Alloy Tubes
E255 Practice for Sampling Copper and Copper Alloys for the Determination of Chemical Composition
E527 Practice for Numbering Metals and Alloys in the Unified Numbering System (UNS)
B 16.22 Wrought Copper and Copper Alloy Solder Joint Pressure Fittings
air conditioning tube; refrigeration tube; welded copper tube; UNS No. C10100; UNS No. C10200; UNS No. C12000; UNS No. C12200; ICS Number Code 2200; 77.150.30 (Copper products)
ASTM International is a member of CrossRef.
Citing ASTM Standards
[Back to Top]