Active Standard ASTM D1275 | Developed by Subcommittee: D27.06
Book of Standards Volume: 10.03
Historical (view previous versions of standard)
Significance and Use
3.1 In most of their uses, insulating liquids are continually in contact with metals that are subject to corrosion. The presence of elemental sulfur or corrosive sulfur compounds will result in deterioration of these metals and cause conductive or high resistive films to form. The extent of deterioration is dependent upon the quantity and type of corrosive agent and time and temperature factors. Detection of these undesirable impurities, even though not in terms of quantitative values, is a means for recognizing the hazard involved.
3.2 Two methods are provided, one for copper corrosion and one for silver corrosion. Copper is slightly less sensitive to sulfur corrosion than silver but the results are easier to interpret and less prone to error. The silver corrosion procedure is provided especially for those users who have applications where the insulating liquid is in contact with a silver surface.
1.1 This test method describes the detection of corrosive sulfur compounds (both inorganic and organic) in electrical insulating liquids.
1.2 New and in-service insulating liquids may contain elemental sulfur or sulfur compounds, or both, that cause corrosion under certain conditions of use. This test method is designed to detect the presence of, or the propensity to form, free (elemental) sulfur and corrosive sulfur compounds by subjecting copper or silver to contact with an insulating liquid under prescribed conditions.
1.3 The values stated in SI units are to be regarded as the standard. Inch-pound units are included for informational purposes.
1.4 This standard does not purport to address the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D130 Test Method for Corrosiveness to Copper from Petroleum Products by Copper Strip Test
Other DocumentANSI B74.10 Grading of Abrasive Microgrits Available from American National Standards Institute, 25 W. 43rd St., 4th Floor, New York, NY 10036, USA.
UNSPSC Code 15121505(Transformer oil or insulating oil)