Published: Jan 1960
| ||Format||Pages||Price|| |
|PDF Version (164K)||7||$25||  ADD TO CART|
|Complete Source PDF (14M)||7||$146||  ADD TO CART|
(a) These methods cover the determination of hardness in industrial water. The following three methods are included: Sections Referee Method (Gravimetric) 5 to 10, Non-Referee Method A (Volumetric Titration) 11 to 17, Non-Referee Method B (Soap Titration) 18 to 23. (b) The referee method is the most dependable for industrial water of unknown composition. The non-referee methods are simpler but less accurate in the presence of interferences. When interferences do not exceed the specified limits in concentration, non-referee method A is as accurate as the referee method. Non-referee method B is preferable if the soap-consuming power of the sample is the principal consideration.
Paper ID: STP44254S