Published: Jan 1979
| ||Format||Pages||Price|| |
|PDF Version (204K)||12||$25||  ADD TO CART|
|Complete Source PDF (3.9M)||12||$55||  ADD TO CART|
The acoustic emission (AE) monitoring of a steam drum-boiler interface in a CANdu nuclear generating station is described. The component was monitored during both the initial hydrostatic test and a load rejection test. Results obtained were not in complete agreement with those previously presented in the literature. Examination of the three-detection method of source location reveals part of the cause of this discrepancy. Other potential mechanisms for the generation of non-locatable AE events are discussed.
acoustics, emission, pressure vessels, hydrostatic test, nuclear power plant
Engineer—nondestructive evaluation, Ontario Hydro Research Division, Toronto,
Paper ID: STP35082S