Active Standard: C926 - 12a
The topic of Paragraph A2.2.3, regarding the soffit drip, best belongs in C1063, as soffit drips are a part of the lath installation, not the plastering installation. A current mandatory requirement, A2.2.3 describes a soffit edge configuration conceived to be a drip edge but in practice is of minimal effectiveness because it does not manage water at the water barrier level, the horizontal casing bead does not drain the wall cavity above it and can corrode, staining the stucco surface. The current language does not require drainage holes and even if drilled would corrode. Further, this assembly is never constructed in contemporary plastering because it is functionally obsolete and has been replaced by various other soffit drip screed assemblies that are more effective. See also the concurrent C1063 ballot item for 6.3.3 adding a viable drip screed requirement to replace A2.2.3.
Keywordsbrown coat; cementitious; exterior plaster; fog coat—bond; portland cement; scratch coat; stucco;
Draft Under Development