SUPERSEDED (see Active link, below)
| ||Format||Pages||Price|| |
|PDF Version||9||$50.40||  ADD TO CART|
1.1 This guide covers procedures to be implemented prior to the application of cathodic protection for evaluating the suitability of a tank for upgrading by cathodic protection alone.
1.2 Three procedures are described and identified as Methods A, B, and C.
1.2.1 Method A- Noninvasive with primary emphasis on statistical and electrochemical analysis of external site environment corrosion data.
1.2.2 Method B- Invasive ultrasonic thickness testing with external corrosion evaluation.
1.2.3 Method C- Invasive permanently recorded visual inspection and evaluation including external corrosion assessment.
1.3 This guide presents the methodology and the procedures utilizing site and tank specific data for determining a tank's condition and the suitability for such tanks to be upgraded with cathodic protection.
1.4 The tank's condition shall be assessed using Method A, B, or C. Prior to assessing the tank, a preliminary site survey shall be performed pursuant to Section 8 and the tank shall be tightness tested pursuant to 5.2 to establish that the tank is not leaking.
1.5 While this guide provides minimum procedures for assessing a tank's condition, this guide does not provide minimum installation procedures or requirements for upgrades of the tank by cathodic protection.
1.6 The values stated in inch-pound units are to be regarded as the standard. The SI units given in parentheses are provided for information only.
1.7 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
D2216 Test Methods for Laboratory Determination of Water (Moisture) Content of Soil and Rock by Mass
E114 Practice for Ultrasonic Pulse-Echo Straight-Beam Contact Testing
E797 Practice for Measuring Thickness by Manual Ultrasonic Pulse-Echo Contact Method
E1323 Guide for Evaluating Laboratory Measurement Practices and the Statistical Analysis of the Resulting Data
E1526 Practice for Evaluating the Performance of Release Detection Systems for Underground Storage Tank Systems
G51 Test Method for Measuring pH of Soil for Use in Corrosion Testing
G57 Test Method for Field Measurement of Soil Resistivity Using the Wenner Four-Electrode Method
ASNT StandardASNTSNT-TC-1A Personnel Qualification and Certification in Nondestructive Testing
NACE International StandardsRP-0285 Standard Recommended Practice-Corrosion Control of Underground Storage Tank Systems by Cathodic Protection
ICS Number Code 77.060 (Corrosion of metals); 77.140.99 (Other iron and steel products)
UNSPSC Code 11101704(Steel)