SUPERSEDED (click for Active standard)
| ||Format||Pages||Price|| |
|7||$51.60||  ADD TO CART|
1.1 This specification establishes the requirements for two wall thickness schedules of specially cleaned, straight lengths of seamless copper tube, identified as Types K and L, suitable for medical gas systems. The tube shall be installed in conformance with the requirements of the National Fire Protection Association (NFPA) Standard 99, Gas and Vacuum Systems (NFPA) Standard 99C, Standard for Hypobaric Facilities (NFPA) Standard 99B, and Canadian Standards Association (CSA) Standard Z 305.1/Z 7396.1, Nonflammable Medical Gas Piping Systems.Note 1
Types K and L tube are defined in Specification B 88.Note 2
Drawn temper tube is suitable for use with capillary (solder joint) fittings for brazing.
1.2 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units, which are provided for information only and are not considered standard.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
B88 Specification for Seamless Copper Water Tube
B251 Specification for General Requirements for Wrought Seamless Copper and Copper-Alloy Tube
B280 Specification for Seamless Copper Tube for Air Conditioning and Refrigeration Field Service
B601 Classification for Temper Designations for Copper and Copper Alloys--Wrought and Cast
B846 Terminology for Copper and Copper Alloys
E8 Test Methods for Tension Testing of Metallic Materials
E18 Test Methods for Rockwell Hardness of Metallic Materials
E29 Practice for Using Significant Digits in Test Data to Determine Conformance with Specifications
E53 Test Method for Determination of Copper in Unalloyed Copper by Gravimetry
E62 Test Methods for Chemical Analysis of Copper and Copper Alloys (Photometric Methods)
E243 Practice for Electromagnetic (Eddy-Current) Examination of Copper and Copper-Alloy Tubes
E255 Practice for Sampling Copper and Copper Alloys for the Determination of Chemical Composition
E527 Practice for Numbering Metals and Alloys in the Unified Numbering System (UNS)
Other StandardsCanadianStandardsAss Nonflammable Medical Gas Piping Systems Available from Canadian Standards Association (CSA), 5060 Spectrum Way, Suite 100 Mississauga, Ontario Canada, L4W 5N6, http://www.csa.ca.
ICS Number Code 11.040.10 (Anaesthetic, respiratory and reanimation equipment)
UNSPSC Code 40182000(Seamless copper tubes); 42000000(Medical Equipment and Accessories and Supplies)
ASTM B819-00(2006), Standard Specification for Seamless Copper Tube for Medical Gas Systems, ASTM International, West Conshohocken, PA, 2006, www.astm.orgBack to Top