SUPERSEDED (click for Active standard)
| ||Format||Pages||Price|| |
|13||$60.00||  ADD TO CART|
1.1 This specification covers corrugated steel pipe intended for use for storm water drainage, underdrains, the construction of culverts, and similar uses. Pipe covered by this specification is not normally used for the conveyance of sanitary or industrial wastes. The steel sheet used in fabrication of the pipe has a protective metallic coating of zinc (galvanizing), aluminum, 55 % aluminum-zinc alloy, or zinc-5 % aluminum-mischmetal alloy.
1.1.1 Steel sheet with zinc and aramid fiber composite coating may be specified for fabrication of pipe. Pipe made from sheet with this composite coating is always furnished with an asphalt coating. Therefore, the requirements in this specification should be considered as applying to a semifinished pipe; the finished pipe must include provisions of Specification A849.
Note 1—Pipe fabricated with zinc and aramid fiber composite coated sheet and asphalt post coating may be used for sanitary sewers and industrial applications. Petroleum products or similar materials in the sewer effluent may affect the performance of the asphalt coating.
1.2 The several different metallic coatings may not provide equal protection of the base metal against corrosion or abrasion in all environments, or both. Some environments may be so severe that none of the metallic coatings included in this specification will provide adequate protection. Additional protection for corrugated steel pipe can be provided by use of coatings applied after fabrication of the pipe as described in Specification A 849, or by use of polymer precoated corrugated steel pipe as described in Specification A762/A762M.
1.3 This specification does not include requirements for bedding, backfill, or the relationship between earth cover load and sheet thickness of the pipe. Experience has shown that the successful performance of this product depends upon the proper selection of sheet thickness, type of bedding and backfill, controlled manufacture in the plant, and care in the installation. The installation procedure is described in Practice A798.
1.4 This specification is applicable to orders in either inch-pound units as A760 or in SI units as A760M. Inch-pound units and SI units are not necessarily equivalent. SI units are shown in brackets in the text for clarity, but they are the applicable values when the material is ordered to A760M.
2. Referenced Documents (purchase separately) The documents listed below are referenced within the subject standard but are not provided as part of the standard.
A90/A90M Test Method for Weight [Mass] of Coating on Iron and Steel Articles with Zinc or Zinc-Alloy Coatings
A153/A153M Specification for Zinc Coating (Hot-Dip) on Iron and Steel Hardware
A307 Specification for Carbon Steel Bolts, Studs, and Threaded Rod 60 000 PSI Tensile Strength
A428/A428M Test Method for Weight [Mass] of Coating on Aluminum-Coated Iron or Steel Articles
ICS Number Code 23.040.10 (Iron and steel pipes)
UNSPSC Code 40171500(Commercial pipe and piping)
ASTM A760 / A760M-00, Standard Specification for Corrugated Steel Pipe, Metallic-Coated for Sewers and Drains, ASTM International, West Conshohocken, PA, 2001, www.astm.orgBack to Top